For a printable version of this case study click here.
A water treatment plant located in Nevada used to treat the water for Clark County. The oxygen system was used to provide gaseous oxygen to the ozone generators. The design of the system was to accommodate a future build-out for tanks and vaporizers.
The project was a public bid that had Chart Industries in the specification. The general contractor approached Chart with the specifications. It was recommended by Chart that we procure and fabricate all the large bore piping to reduce field installation. By doing this, Chart took the responsibility of the vendor coordination, reducing the general contractor’s resource requirements.
Providing equipment per the engineer’s specifications for capacity, material requirement, cleanliness, flow requirements and seismic per Nevada seismic requirements. Taking the responsibility of fabricating the GOX Pressure Manifold greatly reduced the amount of field installation required for this project.
Chart’s two horizontal 13,000 gal vessels with brass/bronze plumbing. Vessels included tank mounted pressure & level transmitters. Chart also included ambient vaporizers rated for 30,000 SCFH each. The GOX Pressure Manifold was 8” SCH40 SMLS piping with butterfly valves mounted to electric actuators as well as temperature transmitters. The GOX manifold included a 316 stainless regulator and was skidded to a stand.
Location – Las Vegas, Nevada
Scope of Project: